Battery Spill Containment
The Uniform Fire Code (UFC) Article 64, Section 104.d and 104.e requires lead-acid battery installations with more than 100 gallons of electrolyte be equipped with a “liquid-tight” spill-control barrier system. It also requires an approved method, capable of neutralizing a spill from the largest lead-acid battery. In response to these new requirements, SBS offers a spill containment system solution. SBS’s system is quick and easy to install with new battery racks.
How Our System Works
Battery Spill Containment System
Example System (Pictured Above) Includes:
A: 42" x 28" x 4" pan (Qty. 1)
B: 25" x 28" x 4" pan (Qty. 1)
C: 27" connector (Qty. 1)
D: 12" x 12" pillows (Qty. 10)
For part numbers and other details, view our data sheet.
Spill Containment Inside Battery Cabinet
inside a battery enclosure.