The Uniform Fire Code (UFC) Article 64, Section 104.d and 104.e requires lead-acid battery installations with more than 100 gallons of electrolyte be equipped with a “liquid-tight” spill-control barrier system. It also requires an approved method, capable of neutralizing a spill from the largest lead-acid battery.
In response to these new requirements, SBS offers a spill containment system solution. SBS’s system is quick and easy to install with new battery racks.
Welded 5/16" thick HDPE pans in multiple sizes
12" x 12" Flame retardant acid absorbing/neutralizing pillows (10" x 10" NiCd pillows available as an option)
Complies with EPA, OSHA, and Uniform Fire Code 64
Acid tight, 4" tall barrier protects from corrosion
SBS stocks different size spill pans that can be placed together in multiple combinations to form different spill containment system lengths and widths.
We provide pillows and connectors that hold the pans together.
Your rack will fit inside our spill containment system. If you are mounting the racks to the floor, you drill through the pans where needed and silicone the bolt and hole to provide a 100% leakproof system.
Battery Spill Containment System
Example System (Pictured Above) Includes:
A: 42" x 28" x 4" pan (Qty. 1) B: 25" x 28" x 4" pan (Qty. 1) C: 27" connector (Qty. 1) D: 12" x 12" pillows (Qty. 10)